Get our free book (in Spanish or English) on rainwater now - To Catch the Rain.
Text replace - "neces?sai" to "necessa"
# The electricity generator, is another essential part as it will convert the mechanical energy of the turbine into electrical energy. This conversion into electricity facilitates the provision on places that can be removed from the turbine. Today, the generator is an alternator that provides alternating current, a type of electricity that is more widespread than direct current. To provide an alternating current conforming to the needs of network users, the alternator must turn in a speed range set by the manufacturer. Between the generator and the turbine, which rotates much more slowly, a gearbox is installed to make the operation of the two machines compatible. The generator is set synchronous or asynchronous, as determined or set on the frequency of the cycles of current of the network, being 50 cycles per second except on the American continent where it is 60 cycles. If the plant is the only or main power source of the network, install a synchronous alternator.
# Electrical cabinet for control and distribution. For the safety of the facilities and also the people, one should distribute the current on the network via a switchboard where the devices (fuses, disconnectors) allow the controlling of the distribution. At the other end of the network similar equipment should be installed to control the distribution with the client.
# The electrical distribution network includes wiring that allows the transport of the power to the users. This network is either low voltage, ie operating voltage of client devices, or high voltage. This is
necessairy when the transport distance is over 500m. Indeed, to carry 20 kW at a voltage of 220V, one requires a 90 amp electrical cable of at least 10mm2 section. If the voltage is 5000V, a section of 1mm2 is sufficient. The cost of this cable will probably be cheaper than the other one.
# The leakage channel is the route of escape of the water that has gone trough the turbine. This channel is connected to the stream that resupplies the watervolume that is diverted to the water intake. It is important that this channel is not flooded in case of riverflood. Indeed, the rise of water level can cause flooding of the engine room (generator and turbine) with a risk of damage.