Project data
Authors Ltpaynetyler ebright Arcata, California Deployed 2009 USD 198.23 Greywater system Download Upload your project too!body.poncho-dark-mode .mw-parser-output .mw-ui-button{background:#303134;border-color:#3c4043;color:#bdc1c6}@media screen and (max-width:500px){.mw-parser-output .button .mw-ui-button{display:block;margin:.5em 0}}

Welcome to the CCAT Greywater Marsh Project Continued! This page will record the efforts made by Linsey Payne and Tyler Ebright during the Spring 2009 semester at HSU to research, complete, and provide an end-use for the treated greywater at CCAT.

## Criteria

Description Weight (0-10 highest) Constraints
Appropriateness 9 Fits CCAT's Mission
Educational Value 7
Safety 9 Water remains sub-surface
Ease of Maintenance 8 Weekly maintenance or less
Functionality 10 Provides end-use
Durability 7 Continues working for 5 to 10 years
Aesthetics 6

### Existing Conditions

Marsh as of February 24th, 2009
Fig 1: Marsh before renovation

The Campus Center for Appropriate Technology (CCAT)'s greywater marsh we inherited has been an on-going project since 2007 when it was relocated to its current location. It is a subsurface marsh off the southwest corner of the house. The greywater comes from the sinks, the shower, and the laundry machine inside the house. The original design had a settling tank first with a sock filter and a siphon system. The siphon was to draw water up out of the tank through the piping over to the second tank, which was about 15 feet away to the south located directly adjacent to the subsurface rock marsh. This second tank was to act as a surge tank. Please see the CCAT greywater marsh (2008) webpage to get the full description of the work that was done as of June of 2008. The current wetland portion of the marsh was left incomplete in anticipation of an end-use for the treated greywater. The surge and settling tanks were also left in need of final adjustments and appurtenances, such as a filter, secure lids, and the completion of the siphon system. Options for the use of the treated water include, gravity fed irrigation or pumping the filtered water into the rainwater catchment system tank for use on all CCAT landscapes and/or for greenhouse irrigation.

### Anticipated Issues

• Punctures and/or wear of existing pond liner.
• Elevation of outlet pipe from existing marsh (approx. 4' below soil surface).
• Location and collection of appropriate end-use landscaping vegetation.
• Settling tank access lid is not secure.
• Filter has likely deteriorated. (made of burlap)
• Surge tank is in a deep hole with little access and is covered by two heavy metal grates.

### Unanticipated Issues

• The siphon system that was planned for in the original design did not work for us with the siphoning method we tested. This method included the testing of a bilge pump and a siphon-hand pump sealed to the top of the tank-to-marsh pipe inside the first tank.
• While testing to see how much water was needed in the first tank for water to flow to the second tank, we discovered that the initial inlet in this tank was not completely sealed. Water leaked from the space between the inlet pipe and the hole cut in the tank. This can be seen more clearly in Figure 2a below.
• While digging the trench for the end use pipe, we encountered a pipe crossing our trench (Fig. 2b). We contacted HSU Plant Operations and found out that there were more pipes that we would encounter. Plant-Ops informed us that to legally dig on this site, we needed to contact USA DIG North for their officials to check out the site before we continued digging.

## Background Research

See Literature Review for research.

## Vision and Proposal

The vision for this project was to confidently present a fully functioning, low-maintenance graywater treatment and irrigation system by the end of the semester in June 2009. The area around the marsh was to be terraced and landscaped with native or naturalized non-invasive vegetation. The water entering the system from the house would be filtered as it entered into the initial surge tank and then flow into a settling tank before entering into the rock marsh. Once in the marsh, the water would flow over two baffles and under three to increase greywater-to-oxygen contact. The greywater would then be released into a third tank where the water could be tested and then released into the gravity fed irrigation system. In case of any overflow during the rainy season, the treated and filtered water would flow down into the storm drain at the base of the driveway, which runs along the west side of the CCAT property.

Proposed Scope of Work:

1. Site Analysis
2. Discussion with CCAT Directors to determine initial ideas for marsh improvement and greywater end-use.
3. Determine functionality of existing system with testing.
4. Complete surge/grease trap/settling tank.
5. Complete terracing and landscaping of area directly surrounding existing marsh.
6. Research potential end-use of greywater and present findings to CCAT Directors and Lonny Grafman.
7. Construct and implement determined end-use of greywater.
8. Complete webpage on appropedia describing all aspects of the project renovation and completion.

## Proposed Time Line

Task Completion Date
Buy Materials April 9, 2009
Connect End-Use Barrel to Marsh April 17, 2009
Draft Website Due April 20, 2009
Dig Irrigation Trench April 21, 2009
Complete System May 11, 2009

## Project Requirements

Project Goals:

• Surge Tank
• Metal Mesh Filter
• Settling Tank
• FOG (Fats, Oil, and Grease) Trap
• Seal all Marsh Inlets and Outlets
• Greywater End-Use
• Gravity Fed Irrigation
• Alkaline Tolerant Vegetation
• Terracing and Landscaping
• Native Vegetation
• Education
• How-to Webpage
• Safety Signage at CCAT
• Maintenance Manual for CCAT

## Design

### Amount of greywater generated by CCAT

1. Calculate the number of occupants of your home:
• 4 people (we added 1 to accommodate for the water use of visitors at CCAT)
2. Estimated daily greywater flows for each occupant are:
• Shower: 15 gal/day/person = 60 gal/day
• Clothes washer = 7 gal/day
• Kitchen sink: 10 gal/day/person = 40 gal/day
• Bathroom sink: 3 gal/day/person = 12 gal/day
3. CCAT daily use total = 119 gal/day

Note: Collecting this data with a daily water-use log would have been more accurate and would be recommended for future greywater projects.

### Issues Addressed

Fig 4a: Marsh pond liner
• Pond Liner: There were no punctures or wear and tear. Although there was an area of liner in the southeast corner of the marsh that was only a few inches taller than the top baffles (which you can see on the right side of the marsh in figure 4a), the level of water in the marsh is not anticipated to reach that height, and is therefore no longer a concern.
• Surge Tank Leakage: Rubber washers included in the bulk head union sets in addition to rubber toilet tank seals keep the water from leaking out the holes for the inlet and outlet piping in the sides of the surge tank.
• Marsh Outlet Elevation: The elevation of the outlet pipe from the existing marsh is approximately 4' below the surrounding grade. This limits the area of the CCAT property that can be irrigated using the greywater. However, it will be able to provide irrigation water for the landscaping directly next to the road and around the signage at the driveway entrance from the 14th street parking lot.
• Surge Tank: The surge tank (2nd Blue Barrel) will now be used as the settling and FOG catching tank and now has hinges and a latch to secure its lid.
Fig 6a: Mesh and plastic filter
• Filter: There was no burlap filter when the settling tank (which is now the surge tank) was initially inspected. A metal mesh filter has replaced the proposed sock/burlap filter.
• Settling Tank: The settling tank (1st White Barrel) will now be used as the surge tank and has been raised so that the bottom of the barrel is only slightly below the inlet pipe from the house. In addition, the decorative heavy metal grates were removed, which resulted in easier maintenance access.
• Once we rejected the siphon method for bringing water from the first tank to the marsh, our options included:
1. raising the first tank to a level where the water filling it would create enough pressure to force flow through the tank-to-marsh pipe,
2. using an electric powered pump,
3. digging up the existing tank-to-marsh pipe to realign it, and
4. moving the first tank closer to the marsh and connecting the inlet pipe to the pipe-to-marsh pipe.
• Because the top of the surge tank and the inlet and outlet pipes were within 12 inches of one another and because there were about 2.5 feet between the pipes and the bottom of the tank, we decided to raise the first tank. If this tank had not been raised, a large volume of greywater would have been left to ferment and turn into blackwater if the system was ever left unused for more than 24 hours. It also did not provide sufficient room for large surges of water. To raise the tank we removed the existing unions attaching the pipes to the tank, cut out the tank to allow its removal, and filled in the hole with dirt and rocks until the tank sat with the pipes about three inches up from the bottom of the tank. The first tank, originally being the settling tank became the surge tank upon this raising and will finally allow water to easily flow from the tank to the marsh.
• Raising the tank meant that we would be cutting a new hole for the inlet pipe, which solved part of the leaking problem mentioned above. To make sure no leaking would occur we put rubber rings on either side of the tank and the existing union keeps these secure.

### Design Process

#### Excavation

The gravel was removed from the end of the marsh behind the last baffle and dirt was excavated directly behind the end of the marsh to a depth of approximately 4 feet. Any water in the marsh was removed using a 1 1/2" Bilge Hand Pump and a bucket (see Figure 7d). The beginning of the irrigation trench was also excavated. Tank #3 was then placed in the hole. This tank was placed vertically with its base approximately level with the bottom of the marsh. The marsh and the barrel were connected through piping a few inches above their bases using a bulk head union. The gravel was replaced between the last baffle and Tank #3. The gravel throughout the marsh was redistributed evenly.

#### Surge Tank

The Surge Tank (aka Tank #1) was initially designed as the settling, filtration, and FOG catching tank. The plan was to have a sock filter attached to the initial greywater outlet from the house and a siphon system to draw water from the barrel and over to Tank #2. The issue with a sock filter is that it requires frequent maintenance and often needs to be replaced. The Oasis Graywater Design Manual states that the "drum with pump and mesh filter [bag] is pretty much a discredited technology at this point due to longevity problems." We have changed the purpose of Tank #1 to be a surge tank with a metal mesh filter to catch large debris. This required that the barrel be raised approximately three feet to bring the bottom of the barrel just a few inches below the inlet and outlet pipes. This will provide at least two feet of surge capacity and will encourage water to flow rapidly through the piping over to Tank #2.

#### Settling Tank

The settling tank (aka Tank #2) was initially designed as the surge tank. Hinges were added to the maintenance opening and the existing duct tape was removed. A larger maintenance opening was added, also with hinges and a latch. This tank mimics a restaurant grease trap with an aluminum baffle trapping the FOG on the water surface, while letting the underlying water flow underneath this baffle, free of FOG, out and into the marsh. This baffle will also slow down the water and allow sediment to settle at the bottom of the tank. The outlet pipe from Tank #2 was attached to the pond liner using a bulk head union (see fig. 9b).

#### Water Testing Tank

Initially improvements were focused on the end-use portion of the marsh system. This required the addition of a water testing site (aka Tank #3) for the cleaned water exiting the marsh. This water will then exit the tank and continue on through an irrigation system to water landscaping plants in the southwest corner of the CCAT property. A blue 55-gallon barrel was donated by CCAT for use as Tank #3. The water testing tank has several functions. The primary function is an access point to the water once it has been cleansed by the biological and physical processes occurring in the marsh for water quality testing. Additional functions are to allow adjustments to be made to the height of the water in the marsh using piping and to be a connection and access point for the beginning of the irrigation system.

#### Mosquito Prevention

Each tank would have some standing water and needed protection from mosquitoes. We gathered some fiberglass mesh, 16 gage wire, and a two inch spring to create protective barriers around the tank openings.

#### Irrigation System

The gravity-fed irrigation system was built to provide water for several alkaline-tolerant plants at the southwest corner of the CCAT property. The irrigation begins at the marsh outlet water testing barrel (aka Tank #3) and flows through ABS piping in a branching pattern at various depths underneath the soil. The depths range from 6" to 4'-0" underneath the surface of the soil. In this system there are 5 outlet points with water being released through holes that were drilled into the last 2' of each pipe branch. These perforated pipes were surrounded by gravel and held in place by heavy rocks or bricks. Dirt was then replaced over the top of the pipes and compacted by walking. 2" to 6" rocks were placed over the branches and main stem of the system to indicate for future users where the pipes are located and as an art piece. The main stem of the system continually slopes gradually downward, while the branches have either a neutral or negative slope.

#### Landscaping

Drought tolerant California native plants were used to landscape the area between the rock wall on the east side of the marsh. These plants will only be receiving rain water after establishment (2 years). Prior to establishment, these plants will need to be watered weekly the first year and monthly the second year. Water loving, alkaline tolerant plants were used to landscape the area receiving the treated gray water. These included small trees, shrubs, and ground covers. Our focus was to use plants that provided food, such as berry bushes or orchard trees. The plants used were: (1) Apple tree, (1) Currant: Ribes speciosum (3) Monkey flowers: Mimulus aurantiacus, (4) Evergreen huckleberries: Vaccinium ovatum, (4) Toyon: Heteromeles arbutifolia, and (2) Coffeeberry: Rhamnus californica. The coffeeberry shrub starts were too small to plant right away and are maturing in their pots as of May 2009. Two rose bushes were already planted on-site and will remain in place.

#### System Activation

There are two valves directly north of the surge tank that turn the water flowing into the greywater system and the sewer system flow on or off from the house (see fig. 14a). If the greywater valve is closed and the sewer valve is open (fig. 14b), the greywater will flow directly into the sewer. If both valves are closed (fig. 14c), the greywater will flow into the house and out the floor drain in the basement bathroom. If the greywater valve is open and the sewer valve is closed (fig. 14d), all of the greywater will flow into the greywater marsh system. If the greywater valve is open and the sewer valve is open (fig. 14e), the greywater will split equally between the greywater and sewer systems due to the plumbing configuration. A gadget (fig. 14f) was made to switch the valves on and off from two pieces of wood. This gadget is inserted all the way into the valve access pipe and fits over the top of the valve handle. The gadget is then turned, using the handle, the desired direction (fig. 14g).

#### Signage

Soap warning and reminder for CCAT household: Soap Recommendations

## Costs

Material Location Unit Cost Quantity Total Cost
Plastic trash bin Arcata Community Recycling Center Free 1 Free
Metal mesh screen Arcata Scrap & Salvage Free 1 Free
Metal frame Arcata Scrap & Salvage Free 1 Free
Aluminum sheet Arcata Scrap & Salvage $4.00 1$4.00
55 Gallon drum HSU CCAT Free 1 Free
4oz E6000 glue Hensel's Hardware $6.49 1$6.49
Hinges Hensel's Hardware $4.29 1$4.29
Bulk screws and nuts combo Hensel's Hardware $0.54 4$2.16
Hex Bolt Hensel's Hardware $0.30 6$1.80
Washer Hensel's Hardware $0.09 12$1.08
Nut with Nylon Hensel's Hardware $0.17 6$1.02
Tank Gasket Hensel's Hardware $2.49 2$4.98
45 Elbow Sch40 1" Hensel's Hardware $1.49 2$2.98
Plastic Rain Collar McKinleyville Ace Hardware $4.79 2$9.58
Backwash KOHLE McKinleyville Ace Hardware $2.49 1$2.49
ABS Adapter West Coast Plumbing $1.59 1$1.59
Rubber 4" x 1.5" coupling West Coast Plumbing $4.95 1$4.95
ABS Coupling Reducer 2" x 1 1/2" West Coast Plumbing $2.15 1$2.15
ABS Standard Adapter 1 1/2" West Coast Plumbing $1.35 1$1.35
Bulkhead Compet 1 1/2" West Coast Plumbing $12.95 2$25.90
ABS Male Adapter 1 1/2" West Coast Plumbing $1.19 2$2.38
ABS 1/4 Bend 1 1/2" West Coast Plumbing $1.19 1$1.19
ABS Pipe 1 1/2" West Coast Plumbing $0.69 3$2.07
Valve Ball Sch40 1" Sunny Brae Ace Hardware $7.99 2$15.98
Tee Sch40 1" Sunny Brae Ace Hardware $0.99 2$1.98
Cross Slip Sch40 1" Sunny Brae Ace Hardware $3.29 1$3.29
Pipe Sch40 1"x10' Sunny Brae Ace Hardware $4.49 5$22.45
Low-VOC PVC Cement Sunny Brae Ace Hardware $3.99 1$3.99
Adapter Sch40 1.5" Sunny Brae Ace Hardware $1.29 1$1.29
Female Adapter Sch40 1.5" Sunny Brae Ace Hardware $1.29 1$1.29
Adapter Sch40 1.5" to 1" Sunny Brae Ace Hardware $1.29 1$1.29
45 Elbow Sch40 1" Sunny Brae Ace Hardware $1.49 2$2.98
"O" Ring Sunny Brae Ace Hardware $0.56 2$1.12
Spring 2" Long Sunny Brae Ace Hardware $3.79 1$3.79
16 Gage Galvanized Wire Sunny Brae Ace Hardware $2.99 1$2.99
Fiberglass Wire Mesh Sunny Brae Ace Hardware $0.89 6 Feet$5.34
Toyon shrub Freshwater Farms $2.50 4$10.00
Monkeyflower shrub Freshwater Farms $3.50 3$10.50
Evergreen Huckleberry shrub Freshwater Farms $4.50 4$18.00
Coffeeberry shrub Freshwater Farms $2.50 2$5.00
Red Flowering Current shrub Freshwater Farms $4.50 1$4.50
Grand Total \$198.23

## Final Thoughts

The completed marsh system is a success, but is not perfect. We provided an end-use for the treated water, vegetated the terrace on the east side of the marsh, connected and sealed each component of the system to one another, and provided the ability of the marsh owners to adjust the level of the marsh water as needed. The system has been simplified from the original version, by the removal of the burlap filter and the siphoning system in the original settling tank. Many of the remaining imperfections are due to the original constraints of the system such as the location of the system, the height of the greywater outlet from the house, a concrete driveway cutting across the connection point between the surge tank and the rest of the system, and the "Y" connection with the overflow valve into the sewer being horizontal instead of vertical. The location and the low elevation of the initial outlet severely restricted the use of the final cleansed water, because most of landscaped portion of the property was located on the eastern side of the house or was above the level of the marsh. The "Y" connection of the sewer and greywater pipes right before the connection with the greywater system hinders the success of the system, because this is the only location for sewer overflow before backing up into the house. This "Y" had been laid horizontally instead of vertically with the sewer connection on top and means that with both valves open the water will split between the two pipes and reduce the efficiency and effectiveness of the greywater system. It also means that if the sewer valve is shut to make sure all greywater leaving the house enters the treatment system and anything goes wrong to clog the surge tank or settling tank, then the water will overflow the surge tank or back up into the house. It is unlikely that the filter in the surge tank will clog, because it is large and not completely sealed. However, if the filter is left for more than a few months without cleaning the danger of clogging has the potential to increase significantly. This will need to be observed by the CCAT co-directors.

### Next Steps

#### Testing

1. Next steps would include water testing from the surge and/or settling tanks as compared to the water in the marsh and then in the final collection tank (tank #3) before the water is released for irrigation.
2. Testing the soil around the vegetation absorbing water from the irrigation system should also be done and compared to the surrounding soil to determine whether or not the greywater is lowering the pH and adding salt compounds to the soil.

#### Maintenance

• Here is a comprehensive maintenance video: http://www.youtube.com/watch?v=PQsiXyZn2a0
• Surge tank filter to be cleaned twice a month with adjustments as needed.
• FOG (Fats, Oils, and Grease) will need to be cleaned from the settling tank at least twice a month, depending on CCAT cooking habits.
• The surge tank and settling tanks will need to be completely drained and cleaned once a year.
• The water level in the marsh will need to be adjusted every three months from lower to higher to encourage different levels of root growth.
• The rocks in the marsh will need to be replaced every 5-10 years as based on water quality testing results.
• The landscaping plants will need to be watered twice a month for the first year and once a month during the second year. After the second year, the plants will only need to be watered during a sustained drought period or if they appear to need another year of watering before they are established enough to rely only on the weather.
• http://www.harvestingrainwater.com/greywater-harvesting/greywater-compatible-soaps-and-detergents/

#### Recommended Improvements

• The baffle in the settling tank may be too small and too low in the barrel. This will need to be observed over time to determine its effectiveness or lack thereof.
• In the irrigation system there are check valves to help distribute the water more evenly between the various outlets. Access pipes should have been placed above them to the top of the soil for future maintenance and adjustment.
• The surge tank will have approximately three inches of greywater sitting inside of it, which is significantly less from the original design, but will still likely turn in to blackwater if the system is left unused for any period longer than 24 hours. The main issue with this will be smell. Concrete has already been added to the tank in order to reduce the amount of excess space. We would recommend an additional fitting to further reduce the extra space. This could be made out of rocks, foam, or more concrete, but the filter will still need to be able to be easily removed and replaced.
• The plumbing in tank #3 has parts that have not been glued to allow for easy adjustment to the level of water in the marsh. As the system ages it may be more effective to have screwing parts or to glue more of the pieces together.
• The fencing around the surge tank and the marsh will need to be replaced or reinforced by Fall of 2009.
• Stairs or easier access points to the surge tank and the settling tank also need to be constructed.

## References

### General Works Cited

• Anderson, C. (2004). Tap into Water Savings, Enjoy lower water bills; lusher landscapes and longer-lived septic systems when you irrigate with your household graywater. Mother Earth News. No. 205, pgs 100-106. August/September 2004.
• Engel, J.P. (2004). Selecting Trees and Shrubs for Alkaline Conditions. White Oak Nursery. www.whiteoaknursery.biz. Copyright 2004.
• Noah, M. (2002). Graywater Use Still a Gray Area. Guest Commentary. Journal of Environmental Health. Vol. 64, No. 10, pgs 22-25. June 2002.

### HSU CCAT Grey Water Binders

• Brown, E., J. Freas, and T. Oxford (2002). CCAT Greywater Marsh Water Quality Project. Engineering 305, 2002.
• Beth, Drew, Nikki, and Stephanie (1997). Grey Water System Analysis of CCAT. Engineering 305, fall semester 1997.
• California (1991). Graywater Systems for Single Family Residential Occupancies (Draft). State of California AD-HOC Committee on Graywater. December 1991.
• Camras, D. (1993). Domestic Greywater Reuse: Presentation Summary. Wastewater Reuse Systems NR 515, Cal Poly Humboldt. April 27, 1993.
• Cecil, K. and E. Mattson (2003). Water Quality Analysis of the CCAT Grey Water Marsh. May 7, 2003.
• Class, D., S. Lim, C. Roberts, and B. Wefso (1993). CCAT Grey Water Treatment System Group Monitoring Project. Engineering 356: Water Quality Analysis. May 14, 1993.
• Conley, L.M., R.I. Dick, and L.W. Lion (1991). An Assessment of the Root Zone Method of Wastewater Treatment. May-June 1991.
• DWR (1995). Graywater Guide Book. State of California, Department of Water Resources. January 1995. http://web.archive.org/web/20090820104825/http://www.owue.water.ca.gov/docs/graywater_guide_book.pdf. Site visited 3/27/09.
• Enferadi, K.M. et al. (1986). Field Investigation of Biological Toilet Systems and Grey Water Treatment. September 1986.
• EPA (1988). Design Manual: Constructed Wetlands and Aquatic Plant Systems for Municipal Wastewater Treatment. United States Environmental Protection Agency. Chapters 2 and 3. September 1988.
• Everett, J. and C. Bysshe (1993-1994). CCAT Wetland Project: A Research Project. 1993-1994.
• Hagberg, T. (1991). The Status of CCAT's Greywater Marsh. Limnology Research Project. May 10, 1991.
• Ho, G., R. Mars, K. Mathew, and R. Taplin (2003). Greywater Treatment with the Submergent Triglochin huegelii - A Comparison Between Surface and Subsurface Systems. (c) Elsevier Science B.V. Ecological Engineering 20 (2003) 147-156.
• Ingham, A.T. (1980). Residential Greywater Management in California. State of California, Sacramento, California. January 1980.
• James, B.B. (1988). Wastewater Disposal in a Forest Evapotranspiration System. January 14, 1988.
• Kozil, J.D., J.S. Svehla, and J.H Wetzel (2003). Water Quality Evaluation of CCAT's Grey Water System. May 7, 2003.
• Landry, C. (1995). Design and Construction of a Rock Marsh Greywater Treatment System for the HSU CCAT. Senior project Department of Environmental Resource Engineering Cal Poly Humboldt. March 1995.
• Leppig, G. (1993). Protozoa Concentrations and Diversity in a Residential Greywater Treatment Marsh. Department of Biological Sciences, Cal Poly Humboldt. May 17, 1993.
• Leveille, K. (1995). Design of an Appropriate Greywater System for the HSU CCAT. Senior project to Department of Environmental Resource Engineering Cal Poly Humboldt. November 1995.
• Los Angeles (1991). Plumbing Code Manual No. 1400. Building and Safety Division. Department of Public Works. County of Los Angeles. August 1991.
• Olkowski, H., B. Olkowski, and T. Javits (unknown). Integral Urban House. Favallones Institute, pgs 97-100.
• Reed, S.C. and D. Brown (1996). Constructed Wetland Design - the 2nd Generation. WPCF. 1996.
• Reed, S.C., E.J. Middlebrooks, and R.W. Crites (1988). Natural Systems for Waste Management and Treatment. Chapter 6. 1988.
• Rose, J.B., S. Gwo-Shing, C.P. Gerba, and N.A. Sinclair (1991). Microbial Quality and Persistence of Enteric Pathogens in Graywater from Various Household Sources. Water Resources. 25 (1), 37-42.
• San Bernardino (1991). Clear Answers to Using Greywater, Part One. County of San Bernardino. October 1991.
• Santa Barbara (1990). How to Save Water and Landscaping Safely. Guidelines: Greywater Use in Santa Barbara. April 1990.
• Santa Barbara (1991). How to Use Gray Water - Guidelines for Santa Barbara County. Santa Barbara County. May 1991.
• Slattery, C. (1990). Questions About Gray Water. Sunset Magazine, pgs 172-175. July 1990.
• Steiner, G.R., J.T. Watson, and K.D. Choate (1991). Constructed Wetlands Wastewater Treatment Systems for Small Users Including Individual Residences. General Design, Construction, and Operation Guidelines. Chattanooga, Tennesse. March 1991.
Page data
Part of Engr305 Appropriate Technology Project ccat, grey water, greywater, fiberglass, wire mesh, metal mesh screen, ccat greywater SDG06 Clean water and sanitation Ltpayne, tyler ebright, Steven Medina 2009 CC-BY-SA-3.0 Campus Center for Appropriate Technology (CCAT), Cal Poly Humboldt Students, Engr305 Appropriate Technology English (en) 244 Ltpayne, tyler ebright, Steven Medina (2009). "CCAT greywater marsh (2014)". Appropedia. Retrieved August 19, 2022.
Cookies help us deliver our services. By using our services, you agree to our use of cookies.